Representatives from the International Firestop Council are available to the media to serve as expert sources for stories on fire protection. IFC can also contribute unpublished, original case studies, white papers and byline articles.
For more information about IFC, to speak to an IFC member, or to request images, please contact the IFC.
Firestopping Inspection Pocket Guide (free PDF download)
Inspection Guidelines for Through-Penetration Firestops, Fire resistant Joint Systems, Perimeter Fire Barriers, and Duct Enclosures – 5th Edition
Hardcopy Pocket Guide booklets are available for $4 each at our Online Store
IFC Guidelines for Evaluating Engineering Judgments - Basic
Recommended IFC EJ Guidelines – Air Ducts
Recommended IFC EJ Guidelines – Grease Ducts
IFC Guidelines for Evaluating Engineering Judgments – Perimeter Fire Barrier Systems
"Point of Contact" penetration firestop systems do not allow a continuous point of contact (zero annular space)
Yours, Mine or Ours — Who is Responsible for the Firestopping?
How To Avoid Firestopping Liability
Continuity Head-of-wall Joint Systems
Differences between UL air duct protection listing categories HNLJ and HNLN
IFC Recommended Guidelines for Performing Destructive Testing for Installed Penetration Firestop Systems, Fire-Resistive Joint Systems,
or Perimeter Fire Barrier Systems
One-page schematic of IBC firestop requirements
The Hose Stream Test
UL Fire Resistive Assemblies and Systems Search
Saving Lives Through Passive Fire Protection
Overview of Fire Protection in Buildings
Repair of Fire-Rated Gypsum Panel Product Systems
Membrane Penetrations in Fire-Resistance Rated Walls
How do I know if an outlet box can be used in a fire-rated assembly?
Top 12 Firestop Deficiencies - By John Valiulis, P.E. and Scott Phillips, ASTM
Barrier Smarts - By George Mills and William E. Koffel, NFPA
The Basics of Passive Fire Protection - By Jenna M. Aker, "Buildings Magazine"
Facility Alterations Can Affect Firestop Systems - By John P. Sinisi, "Facilitiesnet"
Is the IBC Meeting its Intent? "FireEngineering.com"
Firestop Systems – By David J. Volk, P.E., “Canadian Consulting Engineer”
Firestopping & Fireblocking: What’s the Difference? – By Vickie J. Lovell , “PM Engineer Magazine”
Firestopping: Fortifying the Front Line - By Jerry Heid, "zerointernational.com"
Firestopping Fact & Fiction By James Stahl Jr., "Insulation.org"
Common Firestop Code Violations - By Eirene Oliphant, MCP, "ICC Building Safety Journal"
Improving Firestopping for HVAC Duct Penetrations in Fire-Rated Walls - By James Stahl Jr. "Insulation.org"
Stopping Fire in Its Tracks - Part One - By Riley Archer, "International Fire Protection Magazine"
Fighting Fire with Sealants - By Dave Smith, "Adhesives & Sealants Industry"
Use of Differential Scanning Calorimetry Testing to Predict the Aging Behavior of Firestop Materials - By Udo Woersdoerfer & John Valiulis
Teach yourself about
(via PowerPoint presentations)
Firestop Overview – Just the Basics
Flexible Fire Resistive Duct Enclosures
Perimeter Curtain Walls
Firestop System Selection
Comprehensive Firestop Tutorial (96 slides)
Past webinar recordings
Topic: "Special inspection of Firestopping: Understanding and Complying with the 2012 IBC Requirements".
Presenters: John Valiulis (Hilti), Patrick Tesche (Global FPG)
The webinar summarizes and explains the 2012 IBC requirements for Special Inspection of firestopping for penetrations and joints in fire resistance rated construction. It also explains the tools and resources developed by the International Firestop Council to help train people who wish to conduct firestop inspections, and to verify and document their knowledge and understanding via examination.
Find out about the free IFC online education program developed specially for firestop 3rd party inspectors!